Wall Outlet Unit
Outlet shall be manufactured with an 150mm(5.9″) length type 9.5mm [3.8"] outside diameter copper inlet pipe tube, which is chromed to the outlet body. Body shall be 33mm [1-5/16"] diameter on piece brass construction. For positive pressure gas service, the outlet shall be equipped with a primary and secondary check valve and the secondary check valve shall be rated at a minimum 1.379 kPa [200 psi] in the event primary check valve is removed for maintenance. Outlet bodies shall be gas specific by indexing each gas service to a gas specific dual pin indexing arrangement on the respective identification module.
A large color-coded front plate shall be used for easy of gas identification and aesthetic appeal. With the back box mounted the outlet shall adjust up to 32mm [1-1/4"] variation in wall thickness.
* 100% hydrostatic testing of each outlet and cleaned for medical gas service
* Indexed to eliminate interchangeability of gas services
* 360o swivel inlet pipe for easy installation
* Complies with HTM 2015, 2022, European, NFPA and ISO Standards